Interpretation Response #PI-75-038
Below is the interpretation response detail and a list of regulations sections applicable to this response.
Interpretation Response Details
July 28, 1975
Mr. John Searcy
Tennessee Public Service Commission
Cordell Hull Building
Nashville, Tennessee 37219
Dear Mr. Searcy:
The following is in response to your numbered inquiries of July 1, 1975:
- Yes, Section 192.619(c) applies subject to the requirements of Section 192.621.
- For a steel or plastic high-pressure distribution system, the maximum allowable operating pressure is governed by Section 192.619, subject to the applicable limitation of Section 192.621. Under these requirements, a person may not operate a pipeline at a pressure permitted by Section 192.619(c) if that pressure would exceed the applicable limitation of Section 192.621.
Office of Pipeline Safety
|§ 192.619||Maximum allowable operating pressure: Steel or plastic pipelines|