Interpretation Response #PI-85-0102
Below is the interpretation response detail and a list of regulations sections applicable to this response.
Interpretation Response Details
Mr. David Y. Morikawa
PRI Gasco, Inc.
PRI Tower 733 Bishop Street
P. O. Box 3379
Honolulu, Hawaii 96842
Dear Mr. Morikawa:
The Installation of a regulator in an alcove with a louvered door facing the outside of a building would not meet §§192.355(b)(2) or 192.357(d). Under these regulations, the vent outlet of a regulator installed inside a building must be located outside to assure that any gas escaping through the vent is released in the outside atmosphere.
Original signed by
Richard L. Beam
Associate Director for
Pipeline Safety Regulation
Materials Transportation Bureau
|§ 192.355||Customer meters and regulators: Protection from damage|